All in two Solar street light installation steps
⒈Determine the position of the standing light; survey the geological situation,
if the surface of 1 m 2 is soft soil, the excavation depth should be deepened;
at the same time, make sure that there are no other facilities (such as cables, pipes, etc.)
below the excavation position,
and there is no long time at the top of the street light Shade objects, otherwise change position appropriately.
Reserve (excavate) 1m 3 pits in accordance with the standard at the position of the standing lamps;
The embedded part is placed in the middle of the square pit.
One end of the PVC pipe is placed in the middle of the embedded part,
and the other end is placed in the battery storage place (as shown in the figure above).
Pay attention to keep the embedded parts and the ground on the same horizontal plane
(or the top of the screw is on the same level as the original ground, depending on the site requirements),
and one side must be parallel to the road; this way, the rear end of the light pole can be guaranteed to be straight.
Not skewed. Then it is fixed with C20 concrete.
During the pouring process, the vibration of the vibrating rod should not be disabled to ensure the overall compactness and firmness.
⒊After the construction is completed, timely clean up the residual mud on the positioning plate, and clean the impurities on the bolts with waste oil.
⒋During the solidification process of concrete, watering should be carried out at regular intervals;
the installation of chandeliers can only be carried out when the concrete is completely solidified (generally over 72 hours).
Battery component installation
Before connecting the output positive and negative poles of the solar panel to the controller, measures must be taken to avoid short circuit;
⒉ When the solar cell module is connected to the bracket, it should be firm and reliable;
⒊The output line of the component should be kept bare and fastened with cable ties;
⒋The orientation of the battery pack should be directly south, with the compass pointing.
⒈ When the battery is placed in the control box, handle it gently to prevent smashing the control box;
The connecting wires between the batteries must be pressed on the battery terminals with bolts and copper gaskets should be used to enhance the conductivity;
⒊ After the output line is connected to the battery, it is forbidden to short circuit under any circumstances to avoid damage to the battery;
⒋ When the output line of the battery is connected to the controller in the utility pole, it must pass through a PVC conduit;
After the above, check the wiring on the controller side to prevent short circuit. Close the door of the control box after normal
⒈Fix the components of each part: the sun board is fixed on the sun board bracket,
the lamp head is fixed on the pick arm, and then the bracket and the pick arm are fixed on the main rod,
and the connection line is led to the control box (battery box).
Before lifting the lamp pole, check whether the fasteners at all parts are firm, the lamp head is installed correctly, and the light source works normally.
Then check whether the system works normally in the simple debugging; loosen the solar panel connection cable on the controller, and the light source works.
When lifting the main light pole, pay attention to safety precautions; the screws are absolutely tight.
If the angle of the component is deviating from the sun, you need to adjust the sun direction to the south.
⒋ Put the battery into the battery box, and connect the connecting wire to the controller according to the technical requirements; first connect the battery,
then the load, and then the solar panel; be sure to pay attention to the wiring terminals and the terminal terminals marked on the controller when wiring.
If it is connected wrongly, the positive and negative polarities cannot collide and cannot be reversed; otherwise, the controller will be damaged.
⒌ Whether the debugging system works normally; loosen the solar panel connection cable on the controller, the light is on;
connect the solar panel connection cable, the light is off; at the same time,
carefully observe the changes of the indicators on the controller; everything is normal before you can seal the control box.